This chapter shall apply to the installation and operation of industrial ovens and furnaces. Industrial ovens and furnaces shall comply with the applicable provisions of NFPA 86, the International Fuel Gas Code, International Mechanical Code and this chapter. The terms “ovens” and “furnaces” are used interchangeably in this chapter.
The following terms are defined in Chapter 2:
FURNACE CLASS A.
FURNACE CLASS B.
FURNACE CLASS C.
FURNACE CLASS D.
Enclosed rooms or basements containing industrial ovens or furnaces shall be provided with combustion air in accordance with the International Mechanical Code and the International Fuel Gas Code, and with ventilation air in accordance with the International Mechanical Code.
When locating ovens, oven heaters and related equipment, the possibility of fire resulting from overheating or from the escape of fuel gas or fuel oil and the possibility of damage to the building and injury to persons resulting from explosion shall be considered.
Industrial ovens and furnaces shall be located so as not to pose an ignition hazard to flammable vapors or mists or combustible dusts.
Roofs and floors of ovens shall be insulated and ventilated to prevent temperatures at combustible ceilings and floors from exceeding 160°F (71°C).
Fuel-gas piping serving industrial ovens shall comply with the International Fuel Gas Code. Piping for other fuel sources shall comply with this section.
3004.2.1Fuel supply lines.
Valves for fuel supply lines shall be located within 6 feet (1829 mm) of the appliance served.
Exception: When approved and the valve is located in the same general area as the appliance served.
The design of manual fuel shutoff valves shall incorporate a permanent feature which visually indicates the open or closed position of the valve. Manual fuel shutoff valves shall not be equipped with removable handles or wrenches unless the handle or wrench can only be installed parallel with the fuel line when the valve is in the open position.
Interlocks shall be provided for Class A ovens so that conveyors or sources of flammable or combustible materials shall shut down if either the exhaust or recirculation air supply fails.
Class A and B ovens that contain, or are utilized for the processing of, combustible materials shall be protected by an approved automatic fire-extinguishing system complying with Chapter 9.
3006.2Fixed fire-extinguishing systems.
Fixed fire-extinguishing systems shall be provided for Class C or D ovens to protect against such hazards as overheating, spillage of molten salts or metals, quench tanks, ignition of hydraulic oil and escape of fuel. It shall be the user’s responsibility to consult with the fire code official concerning the necessary requirements for such protection.
Portable fire extinguishers complying with Section 906 shall be provided not closer than 15 feet (4572 mm) or not more than 50 feet (15 240 mm) or in accordance with NFPA 10. This shall apply to the oven and related equipment.
OPERATION AND MAINTENANCE
3007.1Furnace system information.
An approved, clearly worded, and prominently displayed safety design data form or manufacturer’s nameplate shall be provided stating the safe operating condition for which the furnace system was designed, built, altered or extended.
Safety data for Class A solvent atmosphere ovens shall be furnished on the manufacturer’s nameplate. The nameplate shall provide the following design data:
1.The solvent used.
2.The number of gallons (L) used per batch or per hour of solvent entering the oven.
3.The required purge time.
4.The oven operating temperature.
5.The exhaust blower rating for the number of gallons (L) of solvent per hour or batch at the maximum operating temperature.
Exception: For low-oxygen ovens, the maximum allowable oxygen concentration shall be included in place of the exhaust blower ratings.
Operating, maintenance and supervisory personnel shall be thoroughly instructed and trained in the operation of ovens or furnaces.
Equipment shall be maintained in accordance with the manufacturer’s instructions.
2015 International Fire Code