Tire rebuilding plants, tire storage and tire byproduct facilities shall comply with this chapter, other applicable requirements of this code and NFPA 13. Tire storage in buildings shall also comply with Chapter 32.
Permits shall be required as set forth in Section 105.6.
3402.1Terms defined in Chapter 2.
Words and terms used in this chapter and defined in Chapter 2 shall have the meanings ascribed to them as defined therein.
Tire rebuilding plants shall comply with the requirements of the International Building Code, as to construction, separation from other buildings or other portions of the same building, and protection.
Buffing operations shall be located in a room separated from the remainder of the building housing the tire rebuilding or tire recapping operations by a 1-hour fire barrier.
Exception: Buffing operations are not required to be separated where all of the following conditions are met:
1.Buffing operations are equipped with an approved continuous automatic water-spray system directed at the point of cutting action.
2.Buffing machines are connected to particle-collecting systems providing a minimum air movement of 1,500 cubic feet per minute (cfm) (0.71 m3/s) in volume and 4,500 feet per minute (fpm) (23 m/s) in-line velocity.
3.The collecting system shall discharge the rubber particles to an approved outdoor noncombustible or fire-resistant container that is emptied at frequent intervals to prevent overflow.
The buffing area shall be cleaned at frequent intervals to prevent the accumulation of rubber particles.
3403.4Spray rooms and booths.
Each spray room or spray booth where flammable or combustible solvents are applied, shall comply with Chapter 24.
PRECAUTIONS AGAINST FIRE
Open burning is prohibited in tire storage yards.
3404.2Sources of heat.
Cutting, welding or heating devices shall not be operated in tire storage yards.
Smoking is prohibited in tire storage yards, except in designated areas.
Tire storage piles shall not be located beneath electrical power lines having a voltage in excess of 750 volts or that supply power to fire emergency systems.
3404.5Fire safety plan.
The owner or individual in charge of the tire storage yard shall be required to prepare and submit to the fire code official a fire safety plan for review and approval. The fire safety plan shall include provisions for fire department vehicle access. Not less than one copy of the fire safety plan shall be prominently posted and maintained at the storage yard.
The telephone number of the fire department and location of the nearest telephone shall be posted conspicuously in attended locations.
Tire storage shall be restricted to individual piles not exceeding 5,000 square feet (464.5 m2) of continuous area. Piles shall not exceed 50,000 cubic feet (1416 m3) in volume or 10 feet (3048 mm) in height.
3405.2Separation of piles.
Individual tire storage piles shall be separated from other piles by a clear space of not less than 40 feet (12 192 mm).
3405.3Distance between piles of other stored products.
Tire storage piles shall be separated by a clear space of not less than 40 feet (12 192 mm) from piles of other stored product.
3405.4Distance from lot lines and buildings.
Tire storage piles shall be located not less than 50 feet (15 240 mm) from lot lines and buildings.
Storage yards shall be maintained free from combustible ground vegetation for a distance of 40 feet (12 192 mm) from the stored material to grass and weeds; and for a distance of 100 feet (30 480 mm) from the stored product to brush and forested areas.
3405.6Volume more than 150,000 cubic feet.
Where the bulk volume of stored product is more than 150,000 cubic feet (4248 m3), storage arrangement shall be in accordance with the following:
Separation between groups shall be not less than 75 feet (22 860 mm) wide.
3405.7Location of storage.
Outdoor waste tire storage shall not be located under bridges, elevated trestles, elevated roadways or elevated railroads.
FIRE DEPARTMENT ACCESS
New tire storage yards shall be provided with fire apparatus access roads in accordance with Section 503 and Section 3406.2. Existing tire storage yards shall be provided with fire apparatus access roads where required in Chapter 11.
Fire apparatus access roads shall be located within all pile clearances identified in Section 3405.4 and within all fire breaks required in Section 3405.5. Access roadways shall be within 150 feet (45 720 mm) of any point in the storage yard where storage piles are located, not less than 20 feet (6096 mm) from any storage pile.
Where the bulk volume of stored material is more than 20,000 cubic feet (566 m3), a firmly anchored fence or other approved method of security that controls unauthorized access to the storage yard shall surround the storage yard.
The fence shall be constructed of approved materials and shall be not less than 6 feet (1829 mm) high and provided with gates at least 20 feet (6096 mm) wide.
Gates to the storage yard shall be locked when the storage yard is not staffed.
Gateways shall be kept clear of obstructions and be fully openable at all times.
A public or private fire protection water supply shall be provided in accordance with Section 508. The water supply shall be arranged such that any part of the storage yard can be reached by using not more than 500 feet (152 m) of hose.
Buildings or structures shall be provided with portable fire extinguishers in accordance with Section 906. Fuel-fired vehicles operating in the storage yard shall be equipped with a minimum 2-A:20-B:C-rated portable fire extinguisher.
INDOOR STORAGE ARRANGEMENT
Where tires are stored on-tread, the dimension of the pile in the direction of the wheel hole shall be not more than 50 feet (15 240 mm). Tires stored adjacent to or along one wall shall not extend more than 25 feet (7620 mm) from that wall. Other piles shall be not more than 50 feet (15 240 mm) in width.
2015 International Fire Code